Hazardous Areas With correct explosion proof glands this cable can be installed in locations subject to explosion hazards rated 0.6/1kV (DIN VDE 0165).
Waste Water Treatment Plants Suitable for submersion in polluted liquids and aggressive environments up to 10 metres.
Lighting & Entertainment With its extra durable CPE sheath this cable is suitable for outdoor temporary power supplies and lighting leads.
Marine Flexible tinned copper & Lloyds approved cable for installation in pleasure craft, super yachts and other marine applications.
Power Used on construction sites due to its outstanding flexibility, durability and industrial performance.
Pumping Suitable for permanent submersion to 500 metres.
- Tinned fine stranded copper conductor
- UV stabilised
- Flame retardant
- Water and moisture resistant
- Good elongation at break
- Resistant to environmental factors such as oxidation, ozone and sunlight
- Suitable for permanent submersion to 500 metres
- Good tensile strength, tearing strength and abrasion resistance
- Heat, oil and chemical resistant (See Chemical Rating Chart)
Conductor Annealed tinned copper stranded high flexibility (Class 5).
Insulation EPR R90.
Sheath CPE Elastomer Rubber.
Operating Temperature Range Fixed -40°C to 90°C / Flexing -25°C to 90°C.
Maximum Conductor Temperature 90°C. (Current ratings are based on 30°C air temp. See technical section for de-rating factors).
Rated Voltage Uo/U 0.6/1kV.
Minimum Bending Radius Fixed 4 x cable diameter / flexing 6 x cable diameter.
Sheath Colour Black.
Standard Core Colours
3 to 19 Core - Black Numbered + Green/Yellow
2 Core – Blue, Brown.
3 Core – Blue, Brown, Green/Yellow.
4 Core – Brown, Black, Grey, Green/Yellow.
5 Core – Blue, Brown, Black, Grey, Green/Yellow.
Multi Core – Black Numbered + Green/Yellow Earth.
Relevant Standards DIN VDE 0295, DIN VDE 0165, IEC 60092-353, IEC 60092-359, IEC 60092-351, AS/NZS 1125, AS/NZS 3808, RoHs Compliant.
AS/NZS 5000.1 Electric cables for working voltage 0.6/1kV.
IEC 60092-350 Electrical installations in ships - Part 350: General construction and test methods.
IEC 60332-3-22 Test for vertical flame spread of vertically-mounted bunched wires or cables.
HO7RN-F Harmonised type heavy duty rubber cable construction. (1.5mm² and above)
Certification Approvals Lloyds Type Approval CEF/SA.